Well water system service is intended to provide you with a help source on your water system failure. Unfortunately, preventive maintenance water supply system in a rural areas is quite often insufficient to alleviate the potential of a system failure. Under failure, one feels trapped to commit to potential unfamiliar resources with time constraints and potential high cost. We offer to help reduce the risk that such a situation imposes.
Our well water system services encompass the well, piping and related components, pumping equipment, pressure tank, and controls for a domestic potable water supply system in rural areas. We can help obtain water permit for well, trouble shoot a failing water supply system, repair or replace components and pumping equipment as might be required to restore your system. We advise and guide you for a new installation and plan for and install the pumping system. Our aim is to assist individual owners get a good a clear picture when faced with a water supply problem. Though the equipment described below are related to a deep well pumps, we do service shallow well equipment as well.
Failure of water supply system in a rural area can be harrowing experience . We can provide an onsite preliminary non-binding free assessment and evaluation of your system requirements.
In listing well water system failure modes, the intent is not to generate fear.
We do this to make you aware that not all modes of failure will result
in a costly well water system service. Clearly, it is possible that a relatively
important fix, subsequent to first appraisal, will get you out of trouble. DIY
person might take it upon himself to do the correction or repair himself with advisory assistance.
pressure tank in a well water system serves to reduce the frequency of pump starts and stops, as well
as, allowing the pump to have a longer run providing a reserve for short
intermittent water use. The tank can fail from corrosion or tank fitting leaks
that result in loss of the air cushion.
differential switch in well water system is usually located on the inlet piping to the pressure tank
can fail from overuse, especially if the pressure tank fails.
pump control box is used to house the start capacitors on a 220V deep well pump motor.
These capacitors are rated for a certain number of immediate start and stop.
However, when there is a failure of pressure tank or pressure differential
switch, leaks, the starts and stops soon
exceed the its limiting capacity and fail.
The wires from motor control box in building to the well are usually in a conduit and protected. However, the wires from top of well to the pump are not protected. Frequent start and stop of pump or pump malfunction can lead to a wire failure.
Piping and fittings can leak. Any well water system leak causes loss of pressure in the system that can lead repeat pump starts, resulting in component failures, such as, pump, pressure tank, and control devices.
fails in a number of ways; for example, the motor can fail due
capacitor failure, pump seal, impellor stuck or broken or worn or damaged bearings.
Well seal can be inappropriate to prevent contamination.
Water can contain dissolved salts, such as carbonates and iron sulphide, bacteria, suspended particles and need pre-treatment prior to use. The devices need can encompass water softener for carbonates, aerator of iron sulfides, reverse osmosis filtration for suspended particles and bacteria and ultraviolet sterilization for bacterial contamination. We can verify requirement by obtaining laboratory analysis and help plan required treatment.
A visit by a competent person with a few diagnostic tools can help identify the key elements that need attention, then advise or propose a repair plan.